We are supplying temperature sensors and thermocouples along with multi channel data logger for temperature monitoring and hydration monitoring of concrete.
Concrete curing monitoring
The temperature of the poured concrete will be monitored during pouring and curing process by the use of copper and zinc thermocouple wires. Huge variation in temperature during the curing process will adversely affect the strength of the concrete block. The thermocouple wires are embedded in concrete at the time of pouring. As the concrete temperature changes, the thermocouple produces a small current which in turn can be measured using a data logger. The multi channel data logger can be programmed to record the temperature at programmed intervals such as every 30 minutes, 60 minutes etc.
In order to record temperatures at various points of the concrete, thermocouple wires will be installed at location as shown in the above sketch or as stipulated by the consultant if applicable. Generally the requirement is that the temperature should be monitored at least every 10 meters. Also at each of these locations, various thermocouples should be placed at different heights. A typical example is shown in the image.
The thermocouple sensor cannot be retrieved after curing of concrete and hence the wire has to be cut and the sensor will be left inside. Hence it is ideal to use long thermocouples with connectors at one end. The other end of the thermocouple wire will be connected to the data logger for recording.
After each test, the thermocouple sensors can be disconnected at the connector and new thermocouples can be used for a new concrete block.
Typically the thermo couple wire will be almost 2 mm thick.
The recorded readings can be downloaded as an excel chart and can be compared to check the differential temperature and verify whether the same are within the permitted limits.